To evaluate (1) the relationship between heating, ventilation, and air conditioning (HVAC) systems and bioaerosol concentrations in hospital rooms, and (2) the effectiveness of laminar air flow (LAF) and high efficiency particulate air (HEPA) according to the indoor bioaerosol concentrations.
Databases of Embase, PubMed, Cochrane Library, MEDLINE, and Web of Science were searched from 1st January 2000 to 31st December 2020. Two reviewers independently extracted data and assessed the quality of the studies. The samples obtained from different areas of hospitals were grouped and described statistically. Furthermore, the meta-analysis of LAF and HEPA were performed using random-effects models. The methodological quality of the studies included in the meta-analysis was assessed using the checklist recommended by the Agency for Healthcare Research and Quality.
The mean CFU/m3 of the conventional HVAC rooms and enhanced HVAC rooms was lower than that of rooms without HVAC systems. Furthermore, the use of the HEPA filter reduced bacteria by 113.13 (95% CI: -197.89, -28.38) CFU/m3 and fungi by 6.53 (95% CI: -10.50, -2.55) CFU/m3. Meanwhile, the indoor bacterial concentration of LAF systems decreased by 40.05 (95% CI: -55.52, -24.58) CFU/m3 compared to that of conventional HVAC systems.
The HVAC systems in hospitals can effectively remove bioaerosols. Further, the use of HEPA filters is an effective option for areas that are under-ventilated and require additional protection. However, other components of the LAF system other than the HEPA filter are not conducive to removing airborne bacteria and fungi.
Limitation of study
Although our study analysed the overall trend of indoor bioaerosols, the conclusions cannot be extrapolated to rare, hard-to-culture, and highly pathogenic species, as well as species complexes. These species require specific culture conditions or different sampling requirements. Investigating the effects of HVAC systems on these species via conventional culture counting methods is challenging and further analysis that includes combining molecular identification methods is necessary.
Strength of the study
Our study was the first meta-analysis to evaluate the effect of HVAC systems on indoor bioaerosols through microbial incubation count. Our study demonstrated that HVAC systems could effectively reduce overall bioaerosol concentrations to maintain better indoor air quality. Moreover, our study provided further evidence that other components of the LAF system other than the HEPA filter are not conducive to removing airborne bacteria and fungi.
Our research showed that HEPA filters are more effective at removing bioaerosols in HVAC systems than the current LAF system. Therefore, instead of opting for the more costly LAF system, a filter with a higher filtration rate would be a better choice for indoor environments that require higher air quality; this is valuable for operating room construction and maintenance budget allocation.
Citation: Dai R, Liu S, Li Q, Wu H, Wu L, Ji C (2021) A systematic review and meta-analysis of indoor bioaerosols in hospitals: The influence of heating, ventilation, and air conditioning. PLoS ONE 16(12): e0259996. https://doi.org/10.1371/journal.pone.0259996
Editor: Muhammad Shahzad Aslam, Xiamen University - Malaysia Campus: Xiamen University - Malaysia, MALAYSIA
Received: June 19, 2021; Accepted: November 1, 2021; Published: December 23, 2021
Copyright: © 2021 Dai et al. This is an open access article distributed under the terms of the Creative Commons Attribution License, which permits unrestricted use, distribution, and reproduction in any medium, provided the original author and source are credited.
Data Availability: All relevant data are within the manuscript and its Supporting Information files.
Funding: This work was supported by the key R & D projects from the Department of Science and Technology of Zhejiang Province [NO.2020C03126] and the Administration of Traditional Chinese Medicine of Zhejiang Province [NO.2017ZZ007], the People’s Republic of China.
Competing interests: The authors have declared that no competing interests exist.
List of abbreviations: COVID-19, coronavirus disease 2019; HVAC, heating, ventilation, and air conditioning; LAF, laminar air flow; CFU, colony forming units; CFU/m3, colony forming units per cubic meter; WHO, World Health Organisation; IAQ, indoor air quality; PRISMA, Preferred Reporting Items for Systematic Reviews and Meta-Analyses; SD, standard deviation; CI, confidence interval; TAF, turbulent air flow; ACH, air change per hour; HEPA, high efficiency particulate air; SSIs, surgical site infections
Heating, ventilation, and air conditioning (HVAC) systems are widely used in hospitals to improve indoor personal comfort, relieve some temperature-related symptoms, and remove bioaerosols [1–3]. However, the coronavirus disease 2019 (COVID-19) pandemic has raised concerns that HVAC systems may increase the risk of airborne diseases if not well designed or properly managed [4–8]. Specifically, studies examining artificially generated aerosols indicated that SARS-CoV-2 is viable in aerosols, and that HVAC systems speed up and change the direction of indoor air flow . As a result, some researchers suspected that HVAC systems may increase the risk of SARS-CoV-2 infection [6, 7], and suggested that poorly designed and managed HVAC systems are likely to provide convenient access to infectious diseases . Therefore, research on the indoor bioaerosol of HVAC rooms to evaluate the advantages and risks of HVAC systems application in indoor environments may help guide the prudent use and management of HVAC systems, especially during the ongoing COVID-19 pandemic.
The laminar air flow (LAF) system is a system that provides unidirectional air flow in the operating room, but it is expensive to install and maintain and requires a lot of energy and ongoing technical maintenance . Standard operating room ventilation filters air with the removal of 80–97% of particles > 5 μm. LAF systems equipped with high-efficiency particulate air (HEPA) filters remove 99.97% of particles > 0.3 μm that may reduce the risk of infectious disease transmissions since they remove particles and large droplets that may carry pathogens [12–15]. The WHO released guidelines in 2016 that suggested that LAF ventilation systems should not be used to reduce the risk of SSIs (surgical site infections) for patients undergoing total arthroplasty surgery based on low quality of evidence . Furthermore, a subsequent meta-analysis discovered that LAF systems have no apparent benefits over conventional turbulent ventilation in operating rooms when trying to reduce the risk of SSIs in total hip and knee arthroplasties or abdominal surgery . LAF systems are currently used for high-risk septic/aseptic operation because some researchers and policy makers still believe that the LAF system is effective in removing bioaerosols anyway [18–22].
Bioaerosols are defined as airborne particles of liquid or volatile compounds that contain living organisms or that have been released from living organisms . Indoor air quality (IAQ) is significantly affected by the concentration of bioaerosols, such as bacteria, fungi, viruses, and pollens. High bioaerosol concentration is associated with greater infectivity, sensitization, and toxicity . At present, there is a study that roughly analysed the concentration and composition of indoor bioaerosols in hospitals, as well as their correlation with HVAC systems . According to Stockwell et al., the indoor colony forming units (CFU) concentration values measured had a large fluctuation range. Moreover, as most of the data were from observational studies, there were many interference factors, leading to poor comparability. Therefore, we decided to expand the scope of retrieval and design stricter inclusion criteria. Furthermore, we designed a combination of statistical description and meta-analysis methods in the protocol . We conducted descriptive statistics on all types of studies, including single group studies, and then selected and compared a qualified experimental group with a control group for meta-analysis.
Our preliminary research objective was to evaluate the effect of HVAC systems on the IAQ of hospitals by determining the concentration of bioaerosols. Furthermore, this study aimed to determine whether the LAF systems and HEPA filters used in hospitals effectively influence these bioaerosol concentrations.
Materials and methods
The present systematic review and meta-analysis were performed according to a protocol designed a priori following recommendations set by the Preferred Reporting Items for Systematic Reviews and Meta-Analyses (PRISMA) guidelines. The present work has been registered at the International Prospective Register for Systematic Reviews, identification code (CRD42020223461) .
A comprehensive search for relevant studies was conducted in the following electronic databases: Embase, PubMed, Cochrane Library, MEDLIN, and Web of Science Core Collection (search query listed in S1 File). Since older HVAC systems may not be technically comparable to modern ventilation systems, researches published before 1st January 2000 were excluded. According to the databases mentioned above and the limiting conditions, we searched a total of 27,610 manuscripts before removing the duplicates. We also screened the reference lists of these literature reviews for further eligible publications.
The selection was conducted by three of our team’s evaluators (R.C.D, S.L, C.H.J) using the EndNote X9.2 software. Removal of duplicates was then performed. After scrutinizing the inclusion and exclusion criteria, two evaluators (R.C.D, S.L) independently classified all studies as either ‘Yes’, ‘No’, or ‘Unclear’. An article was formally included (or excluded) only when both evaluators agreed to that decision; otherwise, the three evaluators (R.C.D, S.L, C.H.J) voted on the matter. There were two stages to this process: a preliminary screening of the title and summary for potentially relevant studies and a detailed screening of the full text. All three evaluators were needed for both stages.
The inclusion criteria for the studies were as follows: (1) studies published (in English) between 1st January 2000 and 31st December 2020, (2) studies wherein air sampling was undertaken indoors in a hospital using the active sampling method, (3) studies that explicitly descried the characteristics of the HVAC system, and (4) studies that quantitatively reported the results in CFU per cubic meter (CFU/m3).
Journal articles were excluded based on the following criteria: 1) the data provided were related only to specific microorganisms (e.g. results limited to legionella); or 2) they were non-original articles (e.g. reviews); or 3) only computational fluid dynamics were used for numerical simulations; or 4) only hospital surfaces were sampled; or 5) lack of classification information (e.g. unable to determine the exact sampling area); or 6) the mean or standard deviation of CFU/m3 was missing and could not be calculated by formulas in S1 Table .
The following information was extracted from each study: the basic information of the articles, conditions for incubating microorganisms after sampling, characteristics of HVAC systems, and concentrations of indoor bioaerosols.
The indoor sampling sites at the hospitals were categorized into publicly accessible areas, inpatient facilities, and restricted areas. Restricted areas/rooms were those that access to which was restricted or required wearing personal protective equipment (e.g. operating room; intensive care unit; haemodialysis room). Ventilation methods were classified as natural ventilation, conventional HVAC systems, and enhanced HVAC systems. Natural ventilation was defined as ventilation that provided air flow by means of opening doors or windows and without an HVAC system. Conventional HVAC systems were defined as HVAC systems (1) without LAF, (2) with a filtration rate of ≤95%, and (3) with an ACH (air change per hour) < 15 exchanges per hour. Enhanced HVAC systems were defined as HVAC systems (1) that equipped with LAF, (2) that have a filtration rate of >95%, or (3) ACH ≥15 exchanges per hour.
In the case of a missing mean or standard deviation (SD) data, the formulas in S1 Table were used for conversion . After the conversions, there were still multiple data with consistent classification. For example, some articles compared working and non-working states  or compared different medical operation procedures . These classifications were not within our research scope, and so we used the Review Manager 5.4.1 Calculator to merge the results of the same classification in the qualitative analysis. Moreover, the sample size could not be determined, we took the minimum number that could be determined as the sample size (e.g., number of rooms sampled or number of surgical cases). We also adjusted the classification of total viable count in some articles according to the type of medium [30–32]. Beyond that, a small number of articles only stated that air conditioning was not used , and we could not accurately judge whether only doors and windows were used for ventilation in that room (or whether the air conditioning had simply been turned off). Because the design structure layout of rooms completely relying on natural ventilation must be different from that of air-conditioned rooms, we divide the data into two groups according to the author’s description: those with natural ventilation and those without HVAC systems.
One reviewer (R.C.D) extracted the data while a second reviewer (H.T.W) ensured the data extraction was accurate and complete. The reviewers discussed all data discrepancies to achieve a consensus, and any uncertainties were resolved by the team members.
Methodological quality assessment
The methodological quality of the studies included in the meta-analysis was assessed using an 11-item checklist recommended by the Agency for Healthcare Research and Quality for cross-sectional/prevalence study quality . An item would be scored ‘0’ if the response was ‘NO’ or ‘UNCLEAR’, and ‘1’ if it was ‘YES’. This was conducted independently by two members of the team. These two reviewers discussed any discrepancies until resolved. The rating details can be found in S1 Appendix.
Statistical description was carried out using SPSS 26 (IBM Corp) and the Wilcoxon signed rank test was used to compare differences according to the characteristics of the final data. Meta-analysis was performed through Stata/MP 14.0. The weighted mean difference and random effects model were used for each comparison. Sensitivity analyses were completed to test the robustness of our finding. Heterogeneity among the studies was tested using of the inconsistency index (I²), and Begg’s Test was employed to assess the occurrence of whether publication. A P-value <0.05 was considered significant.
Fig 1 presents our study selection process. In total, 27,610 records were retrieved during our initial search. After screening the reviews, an additional 46 records from the review were included. Thereafter, 3492 records were excluded using EndNote’s de-duplication tool. A total of 101 articles were assessed for eligibility after the selection of titles and abstracts. Of these articles, we excluded others in accordance with the above-mentioned exclusion criteria. Finally, 30 articles were included in the statistical description and 11 articles were included in the meta-analysis. The characteristics of articles included in the statistical description and meta-analysis are reported in Tables 1 and 2, respectively. The data extracted from the included articles are provided in S2 Table, and we annotated the converted data.
A total of 9336 samples were included in the statistical analysis, and the result of bacteria and fungi are presented in Tables 3 and 4, respectively. This included 4100 bacterial samples and 5236 fungal samples collected from different HVAC systems in various areas of the hospital. In total, 91.20% (n = 3739) and 98.82% (n = 3695) of the bacterial samples were from restricted areas and restricted areas with enhanced ventilation systems, respectively (Fig 2). Overall, 76.68% (n = 4015) and 75.87% (n = 3046) of the fungal samples came from inpatient facilities and inpatient facilities with conventional HVAC systems, respectively (Fig 3). In contrast, few extant studies drew samples from publicly accessible areas in hospitals such that only the fungal counts were available for analysis and all samples were taken from conventional HVAC conditions (n = 575).
The mean CFU/m3 of the conventional HVAC rooms (bacterial count: 217.69 ± 116.69 CFU/m3; fungal count: 37.33 ± 82.78 CFU/m3) and of the enhanced HVAC rooms (bacterial count: 35.94 ± 39.55 CFU/m3; fungal count: 9.46 ± 9.63 CFU/m3) were lower than the rooms without HVAC systems (bacterial count: 360.82 ± 164.40 CFU/m3; fungal count: 38.17 ± 101.36 CFU/m3). In all areas, the indoor mean bioaerosol concentrations of rooms without HVAC system, with conventional HVAC systems and enhanced HVAC systems decreased sequentially (Figs 4 and 5). The concentrations of bacteria and fungi in HVAC rooms in various areas of the hospitals are shown in the Tables 3 and 4.
In hospital environments using HVAC systems, we calculated the mean bioaerosol concentrations under the classifications of LAFand turbulent air flow (TAF) conditions, high ACH and low ACH conditions, and HEPA filter and other filter conditions. All of the results are presented in Table 5. Conditions wherein HEPA filters were used (bacterial count: 36.90 ± 40.06 CFU/m3; fungal count: 9.46 ± 9.63 CFU/m3) showed lower mean bioaerosol concentrations than those wherein other filters were used (bacterial count: 57.83 ± 85.06 CFU/m3; fungal count: 12.21 ± 14.22 CFU/m3). High ACH conditions (bacterial count: 53.45 ± 47.15 CFU/m3; fungal count: 22.96 ± 17.17 CFU/m3) showed significantly lower mean counts of fungi than low ACH conditions (bacterial count: 58.05 ± 53.53 CFU/m3; fungal count: 22.96 ± 17.17 CFU/m3), while there were no significant differences (P = 0.175) in the mean counts of bacteria. For LAF systems, bacterial and fungal counts presented opposite results. The mean and SD of bacterial count in LAF conditions (bacterial count: 26.28 ± 29.78 CFU/m3; fungal count: 5.46 ± 2.77 CFU/m3) were significantly lower than those in TAF conditions (bacterial count: 36.13 ± 38.29 CFU/m3; fungal count: 0.09 ± 0.07 CFU/m3), while the results of fungal count were opposite.
The results of methodological quality evaluation are shown in Table 6, and the scores are between 3–7 points. All the included data were from survey samples, but no inclusion/exclusion criteria were established for the sampling conditions, and no blind method was adopted. We could not be sure if the researchers took follow-up samples from the study environment. In addition, 72.7% of the studies described the time when the survey was conducted, 63.6% repeated sampling, 36.4% explained the reason for excluding the samples, 9.1% described the treatment of missing data, and 27.3% calculated the positive rates of the samples.
The results of the meta-analysis showed that compared with the conventional HVAC systems used in restricted areas, the indoor bacterial count of LAF system conditions decreased by 40.05 CFU/m3 (95%CI: -55.52, -24.58) (Table 6). Moreover, the use of a HEPA filter reduced the bacterial count by 113.14 CFU/m3 (95%CI: -197.89, -28.38) (Table 7 and Fig 6) and the fungal count by 6.53 CFU/m3 (95%CI: -10.50, -2.55) (Table 8 and Fig 7) compared with not using a HEPA filter. Further, in the sensitivity analysis, the conclusion that the LAF system and HEPA filter are effective remained stable. However, all of the results showed high heterogeneity. The results of the Begg’s Test on publication bias indicated a p > 0.05 outcome. All the studies included in the meta-analysis were observational studies, and the results of the methodological quality assessment are shown in Table 9 and Fig 8.
Hospital areas comparisons
It is typically thought that the concentration of microbial bioaerosols should be lower in restricted areas of hospitals because of more stringent management and disinfection measures. However, according to our statistical results, in the hospitals that did not use HVAC systems and enhanced HVAC systems, the mean bacterial count in the restricted areas (36.12 CFU/m3) was higher than that in the inpatient facilities (20 CFU/m3) (Fig 4). This result may have been caused by our small sample size. Samples from the room with enhanced HVAC system in the inpatient facilities were obtained from only one article, with42 bacterial samples in total, accounting for 1.02% of the total bacterial samples. Meanwhile, 34 bacterial samples from 2 papers were obtained from a room with a conventional HVAC system in a restricted area, accounting for 0.83% of the total bacterial samples. Nevertheless, this reminds us that the low bioaerosol concentrations in restricted areas should not be taken for granted. High air quality in restricted areas m requires higher investment compared to that in other areas.
In publicly accessible areas of the hospitals, no bacterial samples met our inclusion criteria, and all 575 fungal samples from these areas came from conditions wherein a conventional HVAC system. We conducted meta-analysis for samples from inpatient facilities and restricted areas because most of the bacterial samples came from restricted areas (n = 3739, 91.20%) (Table 3 and Fig 2) and most of the fungal samples came from inpatient facilities (n = 4015, 76.68%) (Table 4 and Fig 3).
The mean counts of bacteria in the conditions without HVAC systems, with conventional HVAC systems, and with enhanced HVAC systems decreased in turn in the inpatient facilities and restricted areas of the hospitals (p<0.05) (Table 3 and Fig 4). The results for fungi were the same as those for bacteria, but there was a lack of data for publicly accessible and restricted areas (Table 4 and Fig 5). These results indicated that conventional HVAC systems effectively removed bacteria and fungi from indoor air, and that enhanced HVAC systems were more effective than conventional HVAC systems.
Enhanced HVAC systems use HEPA filters or LAF systems, or have higher ACH than conventional HVAC systems. According to our statistical results (Table 5), the HEPA filters used in enhanced HVAC systems proved effective in reducing both bacterial and fungal concentrations in the room. High ACH effectively reduced the indoor fungal concentration, but there was no significant difference in the ability to remove bacteria (p = 0.175). For LAF systems, bacterial and fungal counts showed opposite results, with lower bacterial counts and higher fungal counts in the air in LAF rooms than in TAF rooms. All operating rooms equipped with laminar flow systems were also equipped with HEPA filters, so the protective effect of unidirectional air flow in LAF systems still needs to be further analysed (Table 5).
In the subgroup analysis of fungal CFU concentrations for HEPA filter conditions, we found that the incubation temperatures after sampling significantly affected the results. This is because colonies may not grow properly at uncomfortable incubation temperatures, making it impossible to calculate an accurate microbial concentration. For example, when fungi were incubated at 25°C, the CFU concentration of fungi in the air—which were converted according to the incubation results—in the room with a HEPA filter was lower than that in the room without such a filter (22.15 CFU/m3; 95%CI: -35.79, -8.50). This gap was reduced to 3.32 CFU/m3 (95%CI: -4.60, -2.04) at incubation temperatures of 30°C. If the incubation temperature was increased to 35°C–37°C, the resulting effect range was found to cross the no-effect line (95%CI: -6.52, 0.24) (Table 8 and Fig 8).
Based on the above results, we can conclude that the HEPA filter is effective in reducing the concentration of fungi in hospital indoor air, and its effectiveness can be demonstrated at the appropriate incubation temperature. For bacterial results, the difference in incubation temperature did not seem to be the main cause of excessive heterogeneity (Table 7). Rather, it may be attributed to other condition factors such as the HVAC system’s cleaning frequency, filter’s replacement cycle, number of people in the room, frequency of door opening, additional disinfection regimens, the type of culture medium used in microbial counting, and so on. The source of heterogeneity was not found due to the insufficient number of included articles. Overall, the use of HEPA filters reduced bacteria concentration by 113.14 CFU/m3 (95%CI: -197.89, -28.38) in hospital indoor air.
All the studies in our meta-analysis [21, 33, 52, 59] conducted sampling during operation procedures, while the study by Agodi et al.  also included samples taken during the non-working state. These four studies provide information on the differences in the sample areas of operating rooms. Samples from Hansen et al. , Andersson et al. , and Agodi et al. . collected samples from places as near as possible to the operating area (maximum distance 50 cm), in the surgical wound area, and close to the wound, respectively. Alsved et al.  collected samples from 1 m above the operating table, at the instrument table, and in the periphery of the room. In addition, we excluded the temperature controlled air flow system from our meta-analysis because it is a newly developed ventilation system .
Table 6 shows the bacterial concentrations measured in LAF and non-LAF conditions. Bacterial CFU concentration was 40.05 CFU/m3 (95%CI: -55.52, -24.58) lower in indoor conditions with LAF system than in indoor conditions without LAF system. In our included study, all operating rooms equipped with LAF systems were equipped with HEPA filters. The HEPA filters reduced bacteria by 113.14 CFU/m3 (95%CI: -197.89, -28.38) compared to other filters (Table 7). Therefore, the LAF system has a negative effect on reducing the concentration of bacteria in indoor air, and the use of LAF system instead weakened the HEPA filters’ effect. We hypothesized that the presence of only HEPA filters and conventional HVAC systems in the operating room might have a higher bacterial removal effect.
As for the influence of LAF systems on the CFU concentration of fungi in the air, we did not analyse the systems’ effectiveness of the LAF system based on fungi count because too few fungal samples met our inclusion criteria. However, according to the statistical description of the results, a higher concentration of fungi was observed in the operating room with a LAF system (5.46 ± 2.77 CFU/m3) compared with the operating room with a TAF system (0.09 ± 0.07 CFU/m3) (Table 5). The effectiveness of HEPA filters in removing fungi from the air has been determined (Table 8). Therefore, we ultimately conclude that, other components of the LAF system weakened the HEPA filter’s ability to remove bacteria and fungi.
We investigated airborne concentrations of bacterial and fungal CFU in various areas of the hospital environment and looked for correlations with HVAC systems. We found that the use of HVAC systems could effectively remove these bacteria and fungi. Moreover, the use of HEPA filters in inpatient facilities and restricted areas reduced bacteria by an average of 113.14 CFU/m3 and fungi by 6.53 CFU/m3. The above results fluctuated according to the different incubation temperatures after sampling, especially for the cultivation of fungi, where the temperature may have a great influence on the final converted CFU concentrations.
In the existing LAF system, other parts other than the HEPA filters did not seem to work as they should. This is because according to our statistical results, the use of LAF systems in the operating room only reduced bacteria by 40.05 CFU/m3, less than the CFU reduction of HEPA filters. That is to say, HEPA filters really play a vital role in removing bioaerosols in operating rooms, while other LAF system designs may not be as efficient compared with TAF system. To some extent, this result explains the ineffectiveness of LAF systems in reducing surgical site infections (SSIs).
The study by Hansen et al. reported no differences in bioaerosol concentrations during operation procedures by operation type, number of participating people, and the material of the clothes . Further, in the study by Andersson et al., the number of people present in the operating room the door opening frequency affected bioaerosol concentration significantly, especially in displacement ventilation operating rooms . Additionally, the study by Agodi et al. confirmed that the frequency of door opening and the number of people in an operation room might be key factors in increasing bacterial counts . Finally, Alsved et al. found neither the frequency of door openings nor people present during surgery to be correlated with bioaerosol concentrations . In general, there were diametrically opposite conclusions about the number of people in a room and the frequency of opening doors. We supposed that an operating room can be viewed as a complex system with interactions between patients, different professional teams, and highly specialized techniques, and that it is characterized by the fact that small mistakes or failures can lead to serious adverse events . Because this complex system involves numerous transient phenomena, the air flow distribution of the LAF systems was easily disturbed [39, 40]. In addition, there may be some problems with the current LAF systems. These may include inadequate plenum/canopy size due to undersized areas of ceiling-producing LAF, incorrect positioning of the instruments table (which needs to be entirely under the LAF canopy), and variable cooling of the operating room air—causing local wound area hypothermia and giving surgeons a false sense of sterility security—leading to unnoticed wound contamination during operating procedures .
This study possesses the following limitations. (1) Since all of the included studies were observational, it is likely that there are other factors that have not been analysed, such as a HVAC system’s cleaning frequency, a filter’s replacement cycle, number of people in the room, frequency of door opening, additional disinfection regimens, the type of culture medium used in microbial counting, and so on. (2) Incubation temperature had a great influence on the results of fungi. However, due to the insufficient number of included studies, we did not classify and analyse these CFU concentrations at different incubation temperatures. Further, the effect of incubation temperature on bacterial outcomes was not reflected in the subgroup analysis, which may be due to the interference of the previously mentioned unanalysed influencing factors. Therefore, the bacterial/fungal removal amount included the results at all incubation temperatures. With sufficient stratified calculation of the results at each incubation temperature would be more appropriate. (3) Since we did not study specific microbial species and potential influences of chemical pollution , the overall colony count may be less meaningful. Especially concerning infectious diseases, it may be more beneficial to study specific microbes or viruses instead. Furthermore, even if the total concentrations of microbial cultures in the bioaerosols were similar, different inhalation risks are attributable to the different size distributions and compositions of bioaerosol particles . (4) The results of the methodological quality assessment show that, of the 11 studies included in the meta-analysis, 63.6% of the studies did not explain the situation of discarded samples, 72.7% did not give a positive rate of samples, and 90.9% did not explain the treatment method of missing data. We only extracted the sample size according to the original text and did not make any adjustments. Therefore, there may be some deviation in the statistics of the sample size.
Studies concerning SARS-CoV-2 have shown that infection risks associated with using HVAC systems did not increase during the COVID-19 pandemic . The study by Gola et al. on indoor air chemical pollution showed that a HVAC system was beneficial to improve indoor air quality . Our results regarding bioaerosols showed that the HVAC systems in hospitals today could effectively reduce the indoor concentrations of bioaerosols. This gave us confidence to use air conditioning normally during the COVID-19 pandemic. The use of HEPA filters is an effective option for areas that are under-ventilated and require additional protection. However, the LAF system was not satisfactory in its ability to remove bioaerosols. Other components of the LAF system other than the HEPA filter were not conducive to removing airborne bacteria and fungi. It is important to note that choosing the best between IAQ and energy efficiency was not an easy task , and the routine maintenance and cleaning costs of HVAC systems were often not cheap, especially in indoor conditions with LAF systems. For example, HEPA filters must be replaced regularly because their filter materials can have variable or unknown gas adsorption and particle capture after long-term usage, which can cause a strong matrix effect . Thus, both the purchase and maintenance costs of these enhanced HVAC systems should be taken into account . Therefore, when deciding whether to use HEPA filters or LAF systems, specific cost-benefit analysis should be considered during the actual application process.
S2 Table. The data extracted from 35 studies included.
The authors would like to express our gratitude to all researchers who provided data for our systematic review. We also thank personnel in the hospital-acquired infection control department of the First Affiliated Hospital of Zhejiang Chinese Medical University for providing useful advice on laminar air flow operating rooms management.
- 1. Lacatusu GA, Vasilescu C, Mihai IF, Filip-Ciubotaru F, Vata A, Manciuc C. COVID-19 AND AIR CONDITIONING—IS THERE AN ENVIRONMENTAL LINK? Environmental Engineering and Management Journal. 2020;19(7):1255–60.
- 2. de Araujo Vieira EM, da Silva LB, de Souza EL. The influence of the workplace indoor environmental quality on the incidence of psychological and physical symptoms in intensive care units. Building and Environment. 2016;109:12–24.
- 3. Lenzer B, Rupprecht M, Hoffmann C, Hoffmann P, Liebers U. Health effects of heating, ventilation and air conditioning on hospital patients: a scoping review. Bmc Public Health. 2020;20(1). pmid:32843012
- 4. Bozic J, Ilic P, Ilic S. Indoor Air Quality in the Hospital: The Influence of Heating, Ventilating and Conditioning Systems. Brazilian Archives of Biology and Technology. 2019;62.
- 5. Rule AM. COVID-19 Outbreak Associated with Air Conditioning in Restaurant, Guangzhou, China, 2020. Emerg Infect Dis. 2020;26(11):2791.
- 6. Zhang TL, Lu J, Ying L, Zhu XL, Zhao LH, Zhou MY, et al. An acute gastroenteritis outbreak caused by GII.P16-GII.2 norovirus associated with airborne transmission via the air conditioning unit in a kindergarten in Lianyungang, China. Int J Infect Dis. 2017;65:81–4. pmid:29031606
- 7. Lu J, Yang Z. COVID-19 Outbreak Associated with Air Conditioning in Restaurant, Guangzhou, China, 2020. Emerg Infect Dis. 2020;26(11):2791–3.
- 8. Settimo G. Existing Guidelines for Indoor Air Quality: The Case Study of Hospital Environments: Indoor Air Quality in Healthcare Facilities; 2017.
- 9. Comber L, E OM, Drummond L, Carty PG, Walsh KA, De Gascun CF, et al. Airborne transmission of SARS-CoV-2 via aerosols. Rev Med Virol. 2020:e2184. pmid:33105071
- 10. Correia G, Rodrigues L, Gameiro da Silva M, Goncalves T. Airborne route and bad use of ventilation systems as non-negligible factors in SARS-CoV-2 transmission. Med Hypotheses. 2020;141:109781. pmid:32361528
- 11. Miller AO, Henry MW, Brause BD. 1—Prevention of joint infections. In: Arts JJC, Geurts J, editors. Management of Periprosthetic Joint Infections (PJIs): Woodhead Publishing; 2017. p. 3–23.
- 12. Bernstein JA, Levin L, Crandall MS, Perez A, Lanphear B. A pilot study to investigate the effects of combined dehumidification and HEPA filtration on dew point and airborne mold spore counts in day care centers. Indoor Air. 2005;15(6):402–7. pmid:16268830
- 13. Yeo S, Hosein I, McGregor-Davies L. Use of HEPA filters to reduce the risk of nosocomial spread of SARS-CoV-2 via operating theatre ventilation systems. British Journal of Anaesthesia. 2020;125(4):e361–e3. pmid:32773218
- 14. Qian H, Li Y, Sun H, Nielsen PV, Huang X, Zheng X. Particle removal efficiency of the portable HEPA air cleaner in a simulated hospital ward. Building Simulation. 2010:1–10.
- 15. Malhotra V. A Low-cost Solution for Retrofitment of HEPA Filter in Healthcare Facilities Providing Care to COVID-19 Patients. Indian Pediatrics. 2020;57(5):477. pmid:32277747
- 16. Global Guidelines for the Prevention of Surgical Site Infection. WHO Guidelines Approved by the Guidelines Review Committee. Geneva2016.
- 17. Bischoff P, Kubilay NZ, Allegranzi B, Egger M, Gastmeier P. Effect of laminar airflow ventilation on surgical site infections: a systematic review and meta-analysis. Lancet Infectious Diseases. 2017;17(5):553–61. pmid:28216243
- 18. Andersson AE, Petzold M, Bergh I, Karlsson J, Eriksson BI, Nilsson K. Comparison between mixed and laminar airflow systems in operating rooms and the influence of human factors: Experiences from a Swedish orthopedic center. American Journal of Infection Control. 2014;42(6):665–9. pmid:24713595
- 19. Smith EB, Raphael IJ, Maltenfort MG, Honsawek S, Dolan K, Younkins EA. The Effect of Laminar Air Flow and Door Openings on Operating Room Contamination. Journal of Arthroplasty. 2013;28(9):1482–5. pmid:23890828
- 20. Ahl T, Dalén N, Jörbeck H, Hoborn J. Air contamination during hip and knee arthroplasties. Horizontal laminar flow randomized vs. conventional ventilation. Acta orthopaedica Scandinavica. 1995;66(1):17–20. pmid:7863761
- 21. Alsved M, Civilis A, Ekolind P, Tammelin A, Andersson AE, Jakobsson J, et al. Temperature-controlled airflow ventilation in operating rooms compared with laminar airflow and turbulent mixed airflow. Journal of Hospital Infection. 2018;98(2):181–90. pmid:29074054
- 22. Nilsson KG, Lundholm R, Friberg S. Assessment of horizontal laminar air flow instrument table for additional ultraclean space during surgery. Journal of Hospital Infection. 2010;76(3):243–6. pmid:20846746
- 23. Hallier C, Williams DW, Potts AJC, Lewis MAO. A pilot study of bioaerosol reduction using an air cleaning system during dental procedures. British Dental Journal. 2010;209(8):E14. pmid:20953167
- 24. Abbasi F, Samaei MR. The effect of temperature on airborne filamentous fungi in the indoor and outdoor space of a hospital. Environmental Science and Pollution Research. 2019;26(17):16868–76. pmid:29299864
- 25. Stockwell RE, Ballard L, O’Rourke P, Knibbs LD, Morawska L, Bell SC. Indoor hospital air and the impact of ventilation on bioaerosols: a systematic review. Journal of Hospital Infection. 2019;103(2):175–84. pmid:31279762
- 26. Dai Rongchen, Li Qiushuang, Liu Shan, Wu Li, Wu Hanting, Ji Conghua. A systematic review about indoor microbial bioareosol in hospitals: the influence of heating, ventilation and air conditioning (HVAC). PROSPERO 2020 CRD42020223461 Available from: https://www.crd.york.ac.uk/prospero/display_record.php?ID=CRD42020223461.
- 27. Hozo SP, Djulbegovic B, Hozo I. Estimating the mean and variance from the median, range, and the size of a sample. BMC Med Res Methodol. 2005;5:13. pmid:15840177
- 28. Kedjarune U, Kukiattrakoon B, Yapong B, Chowanadisai S, Leggat P. Bacterial aerosols in the dental clinic: effect of time, position and type of treatment. International dental journal. 2000;50(2):103–7. pmid:10945190
- 29. Augustowska M, Dutkiewicz J. Variability of airborne microflora in a hospital ward within a period of one year. Annals of Agricultural and Environmental Medicine. 2006;13(1):99–106. pmid:16841880
- 30. Cristina ML, Spagnolo AM, Sartini M, Panatto D, Gasparini R, Orlando P, et al. Can Particulate Air Sampling Predict Microbial Load in Operating Theatres for Arthroplasty? PLoS ONE. 2012;7(12). pmid:23285189
- 31. Napoli C, Marcotrigiano V, Montagna MT. Air sampling procedures to evaluate microbial contamination: a comparison between active and passive methods in operating theatres. BMC public health. 2012;12:594. pmid:22853006
- 32. Albertini R, Colucci ME, Turchi S, Vitali P. The management of air contamination control in operating theaters: the experience of the Parma University Hospital (IT). Aerobiologia. 2020;36(1):119–23.
- 33. Hansen D, Krabs C, Benner D, Brauksiepe A, Popp W. Laminar air flow provides high air quality in the operating field even during real operating conditions, but personal protection seems to be necessary in operations with tissue combustion. International Journal of Hygiene and Environmental Health. 2005;208(6):455–60. pmid:16325554
- 34. Rostom A, Dubé C, Cranney A, et al. Celiac Disease. Rockville (MD): Agency for Healthcare Research and Quality (US); 2004 Sep. (Evidence Reports/Technology Assessments, No. 104.) Appendix D. Quality Assessment Forms. Available from: https://www.ncbi.nlm.nih.gov/books/NBK35156/
- 35. Higgins JP, Thompson SG. Quantifying heterogeneity in a meta-analysis. Stat Med. 2002;21(11):1539–58. pmid:12111919
- 36. Fu Shaw L, Chen IH, Chen CS, Wu HH, Lai LS, Chen YY, et al. Factors influencing microbial colonies in the air of operating rooms. BMC Infectious Diseases. 2018;18(1). pmid:29291707
- 37. Khawcharoenporn T, Apisarnthanarak A, Thongphubeth K, Yuekyen C, Damnin S, Hayden MK, et al. Post-flood measurement of fungal bio-aerosol in a resource-limited hospital: Can the settle plate method be used. Journal of Hospital Infection. 2013;83(2):150–2.
- 38. Wan GH, Chung FF, Tang CS. Long-term surveillance of air quality in medical center operating rooms. American Journal of Infection Control. 2011;39(4):302–8. pmid:21256628
- 39. Stocks GW, Self SD, Thompson B, Adame XA, O’Connor DP. Predicting bacterial populations based on airborne particulates: A study performed in nonlaminar flow operating rooms during joint arthroplasty surgery. American Journal of Infection Control. 2010;38(3):199–204. pmid:19913327
- 40. Sautour M, Sixt N, Dalle F, L’Ollivier C, Fourquenet V, Calinon C, et al. Profiles and seasonal distribution of airborne fungi in indoor and outdoor environments at a French hospital. Science of the Total Environment. 2009;407(12):3766–71.
- 41. Perdelli F, Sartini M, Spagnolo AM, Dallera M, Lombardi R, Cristina ML. A problem of hospital hygiene: The presence of aspergilli in hospital wards with different air-conditioning features. American Journal of Infection Control. 2006;34(5):264–8. pmid:16765203
- 42. Pasquarella C, Vitali P, Saccani E, Manotti P, Boccuni C, Ugolotti M, et al. Microbial air monitoring in operating theatres: Experience at the University Hospital of Parma. Journal of Hospital Infection. 2012;81(1):50–7.
- 43. Ortiz G, Yagüe G, Segovia M, Catalán V. A study of air microbe levels in different areas of a hospital. Current Microbiology. 2009;59(1):53–8. pmid:19330376
- 44. Napoli C, Tafuri S, Montenegro L, Cassano M, Notarnicola A, Lattarulo S, et al. Air sampling methods to evaluate microbial contamination in operating theatres: Results of a comparative study in an orthopaedics department. Journal of Hospital Infection. 2012;80(2):128–32.
- 45. Landrin A, Bissery A, Kac G. Monitoring air sampling in operating theatres: Can particle counting replace microbiological sampling? Journal of Hospital Infection. 2005;61(1):27–9. pmid:16009457
- 46. Brun CP, Miron D, Silla LMR, Pasqualotto AC. Fungal spore concentrations in two haematopoietic stem cell transplantation (HSCT) units containing distinct air control systems. Epidemiology and Infection. 2013;141(4):875–9. pmid:22691688
- 47. Dougall LR, Booth MG, Khoo E, Hood H, MacGregor SJ, Anderson JG, et al. Continuous monitoring of aerial bioburden within intensive care isolation rooms and identification of high-risk activities. Journal of Hospital Infection. 2019;103(2):185–92. pmid:31145931
- 48. Sossai D, Dagnino G, Sanguineti F, Franchin F. Mobile laminar air flow screen for additional operating room ventilation: Reduction of intraoperative bacterial contamination during total knee arthroplasty. Journal of Orthopaedics and Traumatology. 2011;12(4):207–11. pmid:22072304
- 49. Cristina ML, Sartini M, Schinca E, Ottria G, Spagnolo AM. Operating room environment and surgical site infections in arthroplasty procedures. Journal of Preventive Medicine and Hygiene. 2016;57(3):E142–E8. pmid:27980378
- 50. Perdelli F, Cristina ML, Sartini M, Spagnolo AM, Dallera M, Ottria G, et al. Fungal contamination in hospital environments. Infection Control and Hospital Epidemiology. 2006;27(1):44–7. pmid:16418986
- 51. Sixt N, Dalle F, Lafon I, Aho S, Couillault G, Valot S, et al. Reduced fungal contamination of the indoor environment with the Plasmair™ system (Airinspace). Journal of Hospital Infection. 2007;65(2):156–62.
- 52. Agodi A, Auxilia F, Barchitta M, Cristina ML, D’Alessandro D, Mura I, et al. Operating theatre ventilation systems and microbial air contamination in total joint replacement surgery: results of the GISIO-ISChIA study. J Hosp Infect. 2015;90(3):213–9. pmid:25997801
- 53. Cho S-Y, Myong J-P, Kim W-B, Park C, Lee SJ, Lee SH, et al. Profiles of Environmental Mold: Indoor and Outdoor Air Sampling in a Hematology Hospital in Seoul, South Korea. International Journal of Environmental Research and Public Health. 2018;15(11).
- 54. Curtis L, Cali S, Conroy L, Baker K, Ou CH, Hershow R, et al. Aspergillus surveillance project at a large tertiary-care hospital. Journal of Hospital Infection. 2005;59(3):188–96.
- 55. Dehghani M, Sorooshian A, Nazmara S, Baghani AN, Delikhoon M. Concentration and type of bioaerosols before and after conventional disinfection and sterilization procedures inside hospital operating rooms. Ecotoxicology and Environmental Safety. 2018;164:277–82. pmid:30121503
- 56. Kabir E, Kim KH, Sohn JR, Kweon BY, Shin JH. Indoor air quality assessment in child care and medical facilities in Korea. Environmental Monitoring and Assessment. 2012;184(10):6395–409. pmid:22086266
- 57. Falvey DG, Streifel AJ. Ten-year air sample analysis of Aspergillus prevalence in a university hospital. Journal of Hospital Infection. 2007;67(1):35–41. pmid:17719681
- 58. Friberg B, Friberg S, Östensson R, Burman LG. Surgical area contamination—Comparable bacterial counts using disposable head and mask and helmet aspirator system, but dramatic increase upon omission of head-gear: An experimental study in horizontal laminar air-flow. Journal of Hospital Infection. 2001;47(2):110–5. pmid:11170774
- 59. Andersson AE, Bergh I, Karlsson J, Eriksson BI, Nilsson K. Traffic flow in the operating room: An explorative and descriptive study on air quality during orthopedic trauma implant surgery. American Journal of Infection Control. 2012;40(8):750–5. pmid:22285652
- 60. Gola M, Settimo G, Capolongo S. Indoor air in healing environments: Monitoring chemical pollution in inpatient rooms. Facilities. 2019;37(9–10):600–23.
- 61. Chirico F, Sacco A, Bragazzi NL, Magnavita N. Can Air-Conditioning Systems Contribute to the Spread of SARS/MERS/COVID-19 Infection? Insights from a Rapid Review of the Literature. Int J Environ Res Public Health. 2020;17(17). pmid:32825303
- 62. Marco Gola, Gaetano Settimo, Stefano Capolongo. Indoor Air Quality in Inpatient Environments: A Systematic Review on Factors that Influence Chemical Pollution in Inpatient Wards. Journal of Healthcare Engineering. 2019.
- 63. Jílková SR, Melymuk L, Klánová J. Emerging investigator series: air conditioning filters as a sampler for semi-volatile organic compounds in indoor and near-building air. Environmental science Processes & impacts. 2020. pmid:33130833
- 64. Settimo G, Avino P. The Dichotomy between Indoor Air Quality and Energy Efficiency in Light of the Onset of the COVID-19 Pandemic. Atmosphere. 2021;12(6):791.