Water Sensitive Urban Design (WSUD) systems are frequently used as part of a stormwater harvesting treatment trains (e.g. biofilters (bio-retentions and rain-gardens) and wetlands). However, validation frameworks for such systems do not exist, limiting their adoption for end-uses such as drinking water. The first stage in the validation framework is pre-validation, which prepares information for further validation monitoring.
A pre-validation roadmap, consisting of five steps, is suggested in this paper. Detailed methods for investigating target micropollutants in stormwater, and determining challenge conditions for biofilters and wetlands, are provided.
A literature review was undertaken to identify and quantify micropollutants in stormwater. MUSIC V5.1 was utilized to simulate the behaviour of the systems based on 30-year rainfall data in three distinct climate zones; outputs were evaluated to identify the threshold of operational variables, including length of dry periods (LDPs) and volume of water treated per event.
The paper highlights that a number of micropollutants were found in stormwater at levels above various worldwide drinking water guidelines (eight pesticides, benzene, benzo(a)pyrene, pentachlorophenol, di-(2-ethylhexyl)-phthalate and a total of polychlorinated biphenyls). The 95th percentile LDPs was exponentially related to system design area while the 5th percentile length of dry periods remained within short durations (i.e. 2–8 hours). 95th percentile volume of water treated per event was exponentially related to system design area as a percentage of an impervious catchment area.
Citation: Zhang K, Randelovic A, Aguiar LM, Page D, McCarthy DT, Deletic A (2015) Methodologies for Pre-Validation of Biofilters and Wetlands for Stormwater Treatment. PLoS ONE 10(5): e0125979. https://doi.org/10.1371/journal.pone.0125979
Academic Editor: Andrew C. Singer, NERC Centre for Ecology & Hydrology, UNITED KINGDOM
Received: November 25, 2014; Accepted: March 27, 2015; Published: May 8, 2015
Copyright: © 2015 Zhang et al. This is an open access article distributed under the terms of the Creative Commons Attribution License, which permits unrestricted use, distribution, and reproduction in any medium, provided the original author and source are credited
Data Availability: All relevant data are within the paper and its Supporting Information files.
Funding: This research was funded by The Cooperative Research Centre for Water Sensitive Cities (E04105)(http://watersensitivecities.org.au/). Zhang is also supported by Chinese Scholarship Council (No.2011609012)(http://www.csc.edu.cn/). The funders had no role in study design, data collection and analysis, decision to publish, or preparation of the manuscript.
Competing interests: The authors have declared that no competing interests exist.
Stormwater is increasingly recognized as a valuable alternative water resource . In Australia, treated stormwater is applied mainly to outdoor non-potable uses (e.g. irrigation) and indoor non-potable uses (e.g. toilet flushing and laundry) . Furthermore, stormwater has been used for outdoor, domestic and municipal irrigation purposes in USA, UK and Sweden [1, 3, 4]. In Singapore, there are also examples of harvesting stormwater for potable use via drinking water reservoirs . Indeed, the potential for harvesting stormwater to potable water use is considerable; for example, it is estimated that in Melbourne, Australia, around 400 GL/yr of stormwater runs off the urban catchment, which is roughly equivalent to the amount of potable water currently consumed in the same city .
Water Sensitive Urban Design (WSUD) technologies, such as biofilters (rain-gardens and bioretentions) and wetlands, are promising stormwater treatment systems that can reduce the high level of stormwater variability to predictable, manageable levels . They are both soil-based natural systems that provide treatment through a combination of physical (sedimentation, mechanical straining), chemical (sorption) and biological process (plants and microbial uptake) . The filter media, the plants and the configuration of these systems could be carefully chosen to enhance the treatment of pollutants in stormwater . They have been proven to efficiently treat sediments, metals, and nutrients [10, 11], microorganisms , and micropollutants . However, these systems are not given any credit for their removal performance when used for stormwater harvesting schemes for almost any end-use. This is mainly due to lack of any methodology on how these systems should be validated before they are allowed to become an integral part of a stormwater treatment train for human consumption.
Water treatment validation is the process of ensuring that (i) a treatment system can produce water of the required quality under a defined range of operational conditions, and (ii) it can be monitored in real time to provide assurance that water quality objectives are being continuously met . There are validation frameworks developed for highly engineered water treatment systems for pathogen removal, such as membrane filtration , ultraviolet (UV) disinfection , activated sludge process and media filtration . However, there are no published guidelines for the validation of WSUD stormwater harvesting systems. The direct application of frameworks developed for highly engineered systems to WSUD stormwater harvesting systems is not possible, because in-situ style challenge tests are usually not applicable to big WSUD systems.
This study presents development of a framework for validation of WSUD systems for stormwater harvesting. As with other validation methodology, (e.g. the one proposed by the Department of Health, Victoria (DHV) ), the proposed framework contains three stages: (i) Pre-validation, (ii) Validation monitoring, and (iii) Operational monitoring. While parallel work is progressing on development of Stages 2 and 3 (Validation monitoring and Operational monitoring ), this paper focuses on Stage 1: Pre-validation. It is the first and very important stage in which the following should be identified: (1) target pollutants, (2) treatment targets, (3) potential removal mechanisms, (4) potential surrogates and (5) operational/challenge conditions. The parameters are directly linked to the end-use of the treated stormwater and treatment system design; for example while for restricted irrigation only sediments and some heavy metals should be considered , for treatment to potable standards all pollutants should be considered with a strong emphasis on removal of pathogens and micropollutants. However, while general stormwater quality has been extensively reported in literature [18–20], the knowledge on both pathogens and organic micropollutants in stormwater is limited. In addition, the complex operational conditions of WSUD systems, which are crucial for validation monitoring, have never been examined.
The aim of this paper is to describe the development of the Pre-validation stage of the Validation Framework for stormwater treatment systems by providing: (i) the roadmap of pre-validation procedure, and (ii) methodologies for completing the pre-validation procedure for micropollutant removal by stormwater biofilters and wetlands, when used in treatment to potable water standards. Specific focus is given to the key research gaps: the identification of the target micropollutants and development of the methodologies for identifying the operational and challenge conditions for the selected WSUD systems. While this study focuses only on biofilter and wetlands, micropollutants as the target pollutant, and treatment to potable standards, the developed pre-validation methodologies are general and could be extended to encompass other WSUD systems, pollutants (e.g. metals and pathogens) and end-uses (e.g. in-door non-potable uses). It is the first attempt in literature to provide a robust framework for the validation of natural treatment systems engaged in stormwater harvesting which, if adopted in practice, could support widespread implementation of stormwater harvesting.
Proposed validation framework for WSUD systems
Table 1 outlines the proposed validation framework for WSUD stormwater treatment systems. The main concepts have been derived from the procedures applied to validation of wastewater recycling systems for non-potable uses .
Stage 1: Pre-Validation
Stage 1: Pre-Validation pertains to gathering necessary information for the next two stages, i.e. Validation monitoring and Operational monitoring. It initially includes selection of target pollutants, corresponding treatment mechanisms and targets. Additionally, the challenge conditions need to be determined, such as maximum loading rates, inflow pollutant levels and challenge hydrological regimes (e.g. challenge treatment flow-rate, event volume, duration of dry-wet periods, etc.). Table 2 outlines the proposed roadmap of the Pre-validation stage, consisting of five steps.
Stage 2: Validation Monitoring
Stage 2: Validation Monitoring determines the system performance under challenge conditions in order to prove that it can cope in extreme situations. Both hydraulics and treatment performance must be validated, which is conducted using in-situ challenge tests. During this step, it is essential that selected surrogates are confirmed using both laboratory and field studies, so that they can be used successfully during operational monitoring. See more details on this stage in Zhang et al .
As already outlined, this study focuses on the Pre-validation stage, with specific focuses on identification of target micropollutants in stormwater (Step 1; Table 2) and identification of operational and challenge conditions for stormwater biofilters and wetlands (Step 5; Table 2) based on the current knowledge gaps in literature. As the operational conditions are system and site specific, the paper selects wetlands and biofilters of different designs and three different climates as examples. While Step 1 and 5 are the main focus of this study, other three steps are also discussed to provide a complete pre-validation roadmap. Step 2 (treatment target) is based on Step 1, whereas Step 3 entails potential removal mechanisms of micropollutants that have been studied extensively in relative natural systems [21–30]. Although there are also knowledge gaps regarding surrogate parameters in natural systems, this study identifies only the potential surrogate parameters for further testing during the later validation monitoring stage.
Step 1: Identification of target micropollutant in stormwater
A literature review was performed to identify micropollutants in stormwater published over last 30 years. Literature search was undertaken through Monash Library that includes key resources (e.g. Scopus, Web of Science, etc.). The following keywords were utilized: stormwater, micropollutant, pesticide, hydrocarbon, phthalate, polychlorinated biphenyl, phenol, halogenated aliphatic, as well as some specific organic compounds based upon the first search. Reference lists of all included articles were manually searched to identify additional sources of data, missing articles, or meeting abstracts. A primary search yielded 562 studies underwent initial abstract review (Fig 1), of which 445 studies were excluded. Of the remaining 114 studies, only 50 reported the micropollutant concentrations in stormwater and were included in the analysis (Table 3).
Various types of micropollutant concentration statistics were presented. Event Mean Concentrations (EMC), representing the flow-weighted average concentration of a single runoff event, are the most representative values for characterisation of stormwater, and thus most commonly reported (Table 3). All EMC values that were found in literature were included in our statistical analysis, even a single value for a given site. If statistics of EMC values were given (e.g. maximum, minimum, medium, etc.), these values were taken. It should be noted that the distribution of EMC values in each piece of literature is seldom indicated. Maximum and minimum concentrations of discrete samples recorded in a single catchment were also considered, since extremes are important for determination of challenge conditions. Only studies which contained greater than 5 rainfall events per site were included; in these cases, the minimum, median and maximum values of the concentrations were estimated. If only the range of discrete concentrations was available (and based on a measurement campaign that had more than 5 events per site), minimum and maximum concentrations were assumed to correspond with the range.
The reviewed papers indicated that >100 micropollutants were identified in stormwater. A micropollutant was selected only if it was measured at more than three catchments. After the screening, data on 37 stormwater micropollutants (Table 3) was used to create the data set.
Due to the scarcity and variability (gathered from various catchments and climates around the world), a triangular distribution was developed for each selected micropollutant. The triangular distribution is a continuous probability distribution with a probability density function shaped like a triangle. It is defined by three values: the minimum value, the maximum value and a mode value (most likely value). This distribution has also been adopted in other studies due to data scarcity [31, 32]. Catchment specific concentrations were not discussed due to the relative limited studies on the micropollutants in stormwater. The absolute minimum and maximum concentrations within the data set were selected as minimum and maximum values for each micropollutant. In cases when the minimum is below detection limit, zero was used; the mode value was determined by establishing the median value among all the median values collected, hence equates with the median of the triangular distribution. The 5th, 50th and 95th percentile concentrations were then established based on the triangular distribution developed. The 95th percentile concentration was selected as challenge concentration, since it is recommended as challenge concentrations in validation monitoring of other water types . The raw data underlying the statistics of micropollutants in stormwater could be found in S1 Table.
Step 2: Specification of the treatment targets
Worldwide drinking water guidelines values [33–36] were sourced to set the treatment targets; these guidelines were used as only drinking water guidelines define specific values for a wide range of micropollutants for human safety protection, while other standards (e.g. irrigation guidelines, ) do not indicate values for micropollutants or they report higher values that may not pose a threat to humans. The targets set by the Australian Guidelines for Water Recycling: Stormwater Harvesting and Reuse  were also used in the study (Table 3).
Step 3: Identification of removal mechanisms and the influential factors
A literature review was carried out to identify potential micropollutants removal mechanisms for different micropollutants groups identified in Step 1. Removal mechanisms of micropollutant have been extensively reported in wetlands [21–26] stormwater bioretention systems [27, 28] and related soil-based systems such as aquifers [29, 30]. These removal processes are largely dependent on the physical-chemical properties of the micropollutants, therefore the latter were also reviewed .
Step 4: Identification potential surrogate parameters
Identification of potential surrogates parameters was conducted by reviewing the current literature on the surrogates for micropollutants during different treatment systems, such as aquifer recharge systems , chemical oxidation [40, 41] and ozonation , as no studies on surrogates have been reported for stormwater biofilters and wetlands.
Step 5: Determination of operational and challenge conditions for biofilters and wetlands in three different climates
The following parameters were considered to be the key operational variables to be considered in defining the boundaries of validation:
- Temperature, which is important for biodegradation in both biofilters  and wetlands , and
- Length of dry periods (LDPs) between two events—e.g. it is reported that long dry periods are detrimental for nitrogen removal by biofilters , while very short dry periods are not desirable for pathogen removal  and micropollutant removal ,
- Volume of water that needs to be treated per event (along with the flow-rate this determines total detention time) is of importance for both wetlands  and biofilters ,
- Extreme wet conditions—it has been found that occurrence of two or more large consecutive events within short period can lead to breaking of the system function during the later events in which the system cannot provide reliable treatment ,
- Flow velocity through the wetland (or infiltration rate through the biofilter) is also crucial for any WSUD treatment system .
It should be noted that other variables, such as soil characteristics, are also important, but they are very system specific and their implications should be tested in Stage 2: Validation monitoring (Table 1).
The challenging values of the selected operational parameters, which are clearly dependent on climatic conditions, were determined for three different regions: humid sub-tropical (Brisbane, annual rainfall 1,000 mm); Mediterranean climate (Perth, annual rainfall 850 mm); and mild oceanic climate (Melbourne, annual rainfall 650 mm). They also had to be determined in relation to size and design of the WSUD systems (i.e. surface area, extended detention depth, permanent pool depth and outlet equivalent pipe diameter). The study followed the Australian standard design practice: i.e. biofilters are designed as per FAWB  guidelines (key design parameters are surface area, hydraulic conductivity, extended detention depth, filter depth and submerged zone) and wetlands as per current Melbourne Water design manual .
To determine (1) Challenge temperature, 30 years minimum and maximum daily temperature data from Bureau of Meteorology (BOM) (station No. 9225 in Perth, No.40245 in Brisbane and No. 86232 in Melbourne) were analysed by creating cumulative distribution curves. The extreme values (5th percentiles of the minimum daily data as well the 95th percentiles of the maximum daily data) were determined for each of the three climatic regions. 5th/95th percentile is selected since it is usually acquired as the cut off in other validation procedures .
To determine the challenge values of (2) LDPs, (3) Volume per event, and (4) Extreme wet condition, the MUSIC V5.1 software package —widely applied in Australian design practice —was used. MUSIC was run for 384 selected designs of biofilters and 30 designs of wetlands for continuous 6 minute rainfall and monthly evaporation data measured between 1980 and 2010 in the three climatic regions. All these designs have covered the potential biofilter and wetland designs in real-life so that the work could be broadly applied. The detailed variable specifications for biofilter and wetland configurations in MUSIC are presented in S2 and S3 Tables, while the model parameters are summarized in S4 and S5 Tables. Properties of the catchment, and the link between catchment and treatment systems, are presented in S6 and S7 Tables.
All modelled events that produced outflows (over 30 years of continuous simulations) were used to construct probability cumulative curves of (i) LDPs and (ii) outflow volume per event for each examined design and climate type. These probability distribution functions (log-normal) were then applied to estimate the 95th percentiles of the LDPs and volume of outflows, to determine their challenge values. The LDPs were determined as the duration between end and start of the outflow of two continuous events, which differs from the normal determination of LDPs (also called the Antecedent Dry Weather Period) that is based on the inflow. Statistics were formulated on outflows in this study because: (i) many events were either too small (having no outflow) or too large (leading to overflow), hence the inclusion of these events very likely resulting in significant errors if inflow was used in statistical analysis; and (ii) in terms of stormwater harvesting, treated water is more important; therefore to be on the safe side, the use of outflows for estimations was favoured. 1% of the maximum outflow-rate of the system (as a function of hydraulic conductivity, surface area, extended detention depth and filter depth; exclude overflow) was used as a cut-off to determine when outflow begins or ends. This cut-off value was determined with reference to experience from previous biofilter field experiments , in which it was established that when the flow-rate of outflow dropped to <1% of maximum flow-rate (i.e. 8.×10–6 m3/s), the measurement instrument could still provide the flow-rate value but no outflow could be observed at the outlet.
The fourth operational parameter, (4) Extreme wet condition, was defined as two consecutive events which are separated by a short dry weather period (i.e. a short LDP). There were two parameters that characterise such an event: (i) the LDP between the two consecutive events and (ii) the volume of stormwater treated in each consecutive event. To determine these parameters, a number of steps were followed:
- The LDP between every consecutive events which occurred in the 30 year rainfall period were calculated;
- All consecutive events which had LDPs greater than the 5th percentile LDP were then removed from further analysis. This was to select only those pairs of consecutive events which were separated by small dry weather periods; and,
- The average volume of all remaining pairs of events was then calculated, and the 95th percentile value was used as the challenge volume.
Biofilters and wetlands are designed to treat a certain capacity of rainfall event and a maximum design flow-rate above which inflow water is bypassed. Therefore the fifth operational parameter—(5) Maximum designed flow-rate—is always specified in the detailed system design for both biofilters and wetlands, hence should be directly adopted as the challenge flow-rate.
It should be acknowledged that the method presented here is quite flexible and subject to change. For example, other models could be used to simulate the hydraulic performance of the ‘to-be-validated’ system, such as Storm Water Management Model (SWMM), which is a dynamic hydrology-hydraulic water quantity and quality simulation model developed by USEPA  and the storage treatment overflow and runoff model (STORM) that is used to simulate the flow volume from watersheds, the bypass flow volume and the flow volume that passes through stormwater treatment systems . Moreover, input data is not restricted to a 6 minute interval over 30 years; a minimum of 10 years of rainfall data, with relatively longer intervals, could be collected for statistical analysis.
Results and Discussions
Step 1: Target micropollutant in stormwater
Table 3 presents the estimated 5th, 50th and 95th percentile concentrations of 37 micropollutants in stormwater. The 95th percentile concentrations of many micropollutants exceed drinking water guideline (DWG) values (Table 3). The estimated 95th percentile concentrations of benzene (10μg/L) and benzo(a)pyrene (BaP) (8μg/L) were above all DWG values (i.e. 1 μg/L for benzene and 0.01 μg/L for BaP according to the most lenient guideline value in Australia). The 95th percentile concentrations of di-(2-ethylhexyl)-phthalate (50μg/L) and pentachlorophenol (90μg/L) exceeded all DWG values except those for the EU which has not defined any guideline values for them. The estimated 95th percentile concentrations of Aldrin and Dieldrin (2 μg/L and 0.2 μg/L respectively) were above Australian and WHO values (i.e. 0.3 μg/L for the sum of these two pesticides). EU DWGs has a maximum value of 0.1μg/L for an individual pesticide and 0.5μg/L for the sum of all pesticides. Hence, all 95th percentile values for pesticides in Table 3 exceeded EU DWG values. Estimated 95th percentile concentration of total PCB was 0.9μg/L, which is above the limit of USEPA guideline value (0.5μg/L). All such micropollutants detected above guideline values should be considered target micropollutants in stormwater. It is also recommended that site specific micropollutant data be used where available in preference to the adopted 95th percentile values estimated in this study.
Step 2: Treatment targets
The DWG values are considered as treatment targets: e.g. the challenge concentration of di-(2-ethylhexyl)-phthalate (DEHP) in stormwater was found to be 50 μg/L (Table 3); for potable reuse in Australia, the treatment system should be able to reduce the concentration to <10 μg/L, and this should be confirmed during validation monitoring in the second stage of the proposed validation framework (Table 1).
Step 3: Potential removal mechanisms of micropollutants and the influential factors
Table 4 summarizes the physical-chemical properties of various micropollutant groups, potential dominating removal mechanisms, and the influential factors, which are based mainly on the study by Mackay et al. , Cottin et al. , Imfeld et al. , Abira M.A. et al. , Alvord et al. , DiBlasi et al. , V.H. Popov et al. ,Larsen et al.  and Pavelic et al. . In validation monitoring, identified potential mechanisms for a specific micropollutant or range of micropollutants will need to be validated separately.
Step 4: Potential surrogate parameters for micropollutant
A suite of readily measurable surrogates for organic micropollutants during wastewater treatment systems, such as aquifer recharge systems, chemical oxidation, and ozonation, was identified by Drewes et al. , Dickenson et al.  and Gerrity et al. . Surrogates, such as the change of ultraviolet absorbance (delta-UVA), dissolved organic carbon (delta-DOC), delta-ammonia, and delta-nitrate, were suitable for monitoring biodegradation while delta-UVA and 3-D fluorescence are effective surrogates for adsorption . These can be considered potential surrogates and should be verified by monitoring. It should be acknowledged that the surrogates suitable for micropollutants in chemical oxidation and ozonation may not be transferable to natural systems, however at this pre-validation stage it is better to form a bigger list of potential surrogates to be identified in later stages. Moreover, a wider range of readily measurable stormwater parameters, e.g. phosphorus, turbidity and electric conductivity, are also recommended to be tested in the second stage of the proposed validation framework (Table 1), where the correlation between a surrogate and corresponding pollutants needs to be elaborated. The suitable surrogate needs to be removed by the same mechanisms, and the surrogates concentration has to be highly correlated to the change in micropollutant concentration.
Step 5: Operational and challenge conditions for biofilters and wetlands in three different climates
The estimated challenge low temperature (5th percentile) and challenge high temperatures (95th percentile) are shown in Table 5. As it is difficult to control the exact temperature during a field challenge test, it is recommended that field challenge tests be performed both in winter at a temperature no higher than the 5th percentile value (e.g. 1.8°C in Brisbane) and summer at a temperature no less than the 95th percentile value (e.g. 34.3°C in Brisbane) to cover the extremes.
The length of dry periods (LDPs).
Fig 2 shows example plots of the estimated LDPs as functions of the percentage of an impervious catchment area for biofilters and wetlands in Oceanic climate (Melbourne). The 95th percentile LDPs are exponentially related to the system area (R2>0.90) for both systems and all climates. Other wetland design parameters had no observed relationship to LDPs (R2<0.05). For biofilters, LDPs increased with the increase of biofilter depth, and decreased with the increase in hydraulic conductivity. Extended detention depth of biofilters had no influence on the LDPs. Generally, if the system is larger in either size or depth, then smaller events would have no outflows and would be regarded as ‘dry’, hence the 95th percentile of the LDPs of a larger system became higher. However, as for the 5th percentile LDPs, the values decreased slightly alongside the increase of system size, whereas the difference between different system designs and types was relatively small, i.e. the 5th percentile dry periods of all biofilters configurations were around 2 hours, whereas those of all wetland were 4–8 hours.
SZ: submerged zone.
To further examine these results in relation to climate and size, for each systems size, the average 95th and 5th percentile of LDPs across all other system design parameters were calculated and presented in Table 6; this was undertaken since system size exerted the strongest impact on results. For the same design of biofilter or wetland area, the 95th percentile LDP follows the order of Mediterranean (Perth)>Subtropical (Brisbane) >Oceanic (Melbourne) with an exception of Oceanic (Melbourne) being the longest at the largest biofilter area (10% of impervious catchment area).
Volume of water treated per event.
The 95th percentile volumes per event were plotted against the system surface areas, and the exponential curves fitted are shown in Fig 3 for biofilters located in Mediterranean climate (Perth) and in Fig 4 for wetlands located in Subtropical (Brisbane) and Oceanic (Melbourne) climates.
SZ: submerged zone.
Biofilters: Volume per area decreased with surface areas, filter depth and extended detention depth. The systems of equivalent total filter depth, but with and without submerged zone, had different treatment volumes; the systems without submerged zones were able to treat more water since they had higher hydraulic gradients. However, the depth of submerged zone had little relationship to the volumes, probably because the dry periods simulated were not long enough to dry the submerged zone.
The average volume for both single events and consecutive events was calculated for each system size and summarized in Table 6. Volumes for consecutive events were lower than that of one single event; the reason might be that the incidents of rainfall during consecutive events are more expansively spread. For a Mediterranean climate (Perth), the total average 95th percentile volumes of consecutive events are about 74% of one single event, while percentages for oceanic (Melbourne) and subtropical (Brisbane) climates are 70% and 80% respectively. The 95th percentile volume of either single event or consecutive events for biofilter follows the order of subtropical (Brisbane, 1008.2 mm/y)> Mediterranean (Perth, 850.0 mm/y)> oceanic (Melbourne, 649.6 mm/y) with an exception of Perth being the highest at the smallest biofilter design (1% of impervious catchment area) (Table 6).
Wetlands: The volume per unit area decreased with increasing surface area (Fig 4). In the majority of cases, the greater the extended detention depth, the greater the volume per area of water treated with the greatest difference in the smallest wetland areas. Permanent pool depth (PPD) had very little effect upon the volume treated per event.
The average 95th percentile volume for both a single event and consecutive events for each wetland size appears in Table 6. Volumes for consecutive events are generally lower than that of a single event, with a few exceptions in small surface areas. Perth had the largest 95th percentile volume of either single event or consecutive event, while Brisbane showed the smallest 95th percentile volumes, except for the large surface areas, i.e. 5% and 10% of the impervious catchment area.
Implications for the design of testings as Validation Monitoring
By applying the roadmap into the ‘to-be-validated’ system, all necessary information could be gathered through the five steps, and then proper validation monitoring testings can be designed. For example, the validation monitoring tests shall be performed in both winter (at temperature ≤5th percentile value; Table 5) and summer time (at ≥95th percentile value; Table 5) from Step 5; with determined 95th percentile challenge volumes (Fig 3 for biofilter and Fig 4 for wetland; Step 5) of inflow water containing 95th percentile challenge concentrations of target micropollutants (Table 3; Step 1) dosed into the ‘to-be-validated’ stormwater treatment systems. A series of testings is to be conducted to cover both challenge wet (5th LDPs; Fig 2) and dry conditions (95th LDPs; Fig 2; Step 5) to check if the treated water meets the treatment target (Step 2). Meanwhile, removal mechanisms of target micropollutants in Step 3 should be validated during in-situ tests (if possible) or laboratory studies. The identified potential surrogates (step 4) should be tested during validation monitoring to identify the most suitable surrogate parameters to be used in operational monitoring.
If stormwater is to be treated for potable uses, Water Sensitive Urban Design (WSUD) should be used for preliminary treatment, and followed by advance treatment technologies to ensure required water standards are met. However, WSUD systems are the crucial step in such treatment trains, since they will reduce the high variability in stormwater quality and therefore ensure that the advance technologies perform well. One of the critical steps for using WSUD systems for safe stormwater harvesting is treatment validation. The successful validation of these systems will provide confidence to water regulators and the community at large, so that the treated stormwater can go directly to drinking water supplies.
The world’s first validation framework, consisting of three stages (i.e. pre-validation, validation monitoring and operational monitoring) for WSUD systems, was proposed. This paper focused on the pre-validation stage and developed a specific roadmap consisting of five steps with detailed methodologies: (1) identification of target micropollutants, (2) specification of treatment targets, (3) identification of potential removal mechanisms and influential factors, (4) identification of potential surrogates and (5) determination of operational and challenge conditions.
A literature search was undertaken to identify and quantify micropollutants in stormwater. Statistical analysis revealed that challenge concentrations of 8 pesticides, benzene, benzo(a)pyrene, pentachlorophenol (PCP), di-(2-ethylhexyl)-phthalate (DEHP) and total polychlorinated biphenyls (PCBs), were above different worldwide drinking water guideline limits, and hence set the treatment targets. Potential removal mechanisms (e.g. adsorption and biodegradation) for different micropollutant groups, as well as potential surrogates (e.g. delta-UV and delta-DOC), were identified through a literature review for further Validation monitoring and Operational monitoring.
A method that utilises MUSIC is suggested in this paper as a means of determining challenge conditions of stormwater treatment systems of varying design, using historical climate data. Results showed that 95th percentile length of dry periods was exponentially related to system design area—as a percentage of an impervious catchment area—while the 5th percentile length of dry periods remained within short durations (i.e. 2–8 hours). 95th percentile volume of water treated per event was exponentially related to system design area as a percentage of an impervious catchment area.
S1 Table. PRISMA Checklist.
S2 Table. Raw data for analysis of micropollutant concentration in stormwater.
S3 Table. Variable specifications for biofilter nodes in MUSIC.
S4 Table. Variable specifications for wetland nodes in MUSIC.
S5 Table. Fixed specifications for biofilter nodes in MUSIC.
S6 Table. Fixed specifications for wetland nodes in MUSIC.
S7 Table. Fixed specifications for catchment in MUSIC.
S8 Table. Fixed specifications for drainage link/stormwater network pipe in MUSIC.
The authors wish to acknowledge Cintia Dotto for her assistance in running and writing code for MUSIC and MATLAB. Aidan Sudbury is also gratefully acknowledged for his advice on statistical analysis.
Conceived and designed the experiments: KFZ AR DP DTM AD. Performed the experiments: KFZ AR LMA. Analyzed the data: KFZ AR LMA. Contributed reagents/materials/analysis tools: KFZ AR DP DTM AD. Wrote the paper: KFZ.
- 1. Hamdan S. A literature based study of stormwater harvesting as a new water resource. Water Science & Technology. 2009;60(5):1327–39.
- 2. Hatt BE, Deletic A, Fletcher TD. Integrated treatment and recycling of stormwater: a review of Australian practice. Journal of Environmental Management. 2006;79(1):102–13. http://dx.doi.org/10.1016/j.jenvman.2005.06.003. pmid:16256264
Hinch J. Stormwater reuse infrastructure & effects on stormwater reuse infrastructure due to climate change. Municipal Engineering Foundation Victoria, 2009.
- 4. Steffen J, Jensen M, Pomeroy CA, Burian SJ. Water Supply and Stormwater Management Benefits of Residential Rainwater Harvesting in U.S. Cities. JAWRA Journal of the American Water Resources Association. 2013;49(4):810–24.
Philp M, McMahon J, Heyenga S, Marinoni O, Jenkins G, Maheepala S, et al. Review of stormwater harvesting practices. Urban Water Security Research Alliance, 2008.
ENRC. Inquiry into Melbourne's future water supply. Melbourne: Environment and Natural Resources Committee, 2009.
- 7. Zhang S, Guo Y. Stormwater Capture Efficiency of Bioretention Systems. Water Resources Management. 2014;28(1):149–68.
NRMMC-EPHC-NHMRC. Australian Guidelines for Water Recycling(Phase 2): Stormwater Harvesting and Reuse. Canberra: Natural Resource Management Ministerial Council, Environment Protection and Heritage Council, and National Health and Medical Research Council; 2009.
- 9. Li YL, Deletic A, Alcazar L, Bratieres K, Fletcher TD, McCarthy DT. Removal of Clostridium perfringens, Escherichia coli and F-RNA coliphages by stormwater biofilters. Ecological Engineering. 2012;49(137–145).
- 10. Davis A, Hunt W, Traver R, Clar M. Bioretention Technology: Overview of Current Practice and Future Needs. Journal of Environmental Engineering. 2009;135(3):109–17.
- 11. Payne EGI, Fletcher TD, Russell DG, Grace MR, Cavagnaro TR, Evrard V, et al. Temporary Storage or Permanent Removal? The Division of Nitrogen between Biotic Assimilation and Denitrification in Stormwater Biofiltration Systems. PLoS ONE. 2014;9(3):e90890. pmid:24670377
- 12. Chandrasena GI, Deletic A, Ellerton J, McCarthy DT. Evaluating Escherichia coli removal performance in stormwater biofilters: a laboratory-scale study. Water Science & Technology. 2012;66(5):1132–8.
- 13. Zhang K, Randelovic A, Page D, McCarthy DT, Deletic A. The validation of stormwater biofilters for micropollutant removal using in situ challenge tests. Ecological Engineering. 2014;67:1–10. http://dx.doi.org/10.1016/j.ecoleng.2014.03.004.
DHV. Guidelines for validating treatment processes for pathogen reduction—Supporting Class A water recycling schemes in Victoria. Department of Health,Victoria, 2013.
USEPA. Membrane Filtration Guideline Manul. Cincinnati: Office of Water, 2005.
USEPA. Ultraviolet disinfection guidance manual for the final long term 2 enhanced surface water treatment rule. In: Office of Water, editor. 2006.
NRMMC-EPHC-NHMRC. National Guidelines for Water Recycling: Managing Health and Environmental Risks (Phase 2 Stormwater Harvesting and Reuse). Canberra: Natural Resource Management Ministerial Council, Environment Protection and Heritage Council, and National Health and Medical Research Council; 2009.
- 18. Makepeace DK, Smith DW, Stanley SJ. Urban stormwater quality: Summary of contaminant data. Critical Reviews in Environmental Science and Technology. 1995;25(2):93–139.
Duncan H. Urban stormwater quality: a statistical overview. Cooperative Research Centre for Catchment H, editor. Melbourne: CRC for Catchment Hydrology; 1999.
- 20. Göbel P, Dierkes C, Coldewey WG. Storm water runoff concentration matrix for urban areas. Journal of Contaminant Hydrology. 2007;91(1–2):26–42. pmid:17196707
- 21. Imfeld G, Braeckevelt M, Kuschk P, Richnow HH. Monitoring and assessing processes of organic chemicals removal in constructed wetlands. Chemosphere. 2009;74(3):349–62. pmid:18996559
- 22. Zhao W, Wu Z, Zhou Q, Cheng S, Fu G, He F. Removal of dibutyl phthalate by a staged, vertical-flow constructed wetland. Wetlands. 2004;24(1):202–6.
- 23. Cottin N, Merlin G. Removal of PAHs from laboratory columns simulating the humus upper layer of vertical flow constructed wetlands. Chemosphere. 2008;73(5):711–6. pmid:18682309
- 24. Abira MA, B JJA, D P. Potential of a tropical subsurface constructed wetland to remove phenol from pre-treated pulp and papermill wastewater. Water Science & Technology. 2005;51(9):173–6.
- 25. Alvord HH, Kadlec RH. Atrazine fate and transport in the Des Plaines Wetlands. Ecological Modelling. 1996;90(1):97–107.
- 26. Tsui M, Chu L. Environmental fate and non-target impact of glyphosate-based herbicide (Roundup) in a subtropical wetland. Chemosphere. 2008;71(3):439–46. pmid:18155747
- 27. DiBlasi CJ, Li H, Davis AP, Ghosh U. Removal and Fate of Polycyclic Aromatic Hydrocarbon Pollutants in an Urban Stormwater Bioretention Facility. Environmental Science & Technology. 2008;43(2):494–502.
- 28. Popov VH, Cornish PS, Sun. H. Vegetated biofilters: The relative importance of infiltration and adsorption in reducing loads of water-soluble herbicides in agricultural runoff. Agriculture, Ecosystems and Environment. 2006;114:351–9.
- 29. Larsen L, Aamand J. Degradation of herbicides in two sandy aquifers under different redox conditions. Chemosphere. 2001;44(2):231–6. pmid:11444305
- 30. Pavelic P, Dillon PJ, Nicholson BC. Comparative evaluation of the fate of disinfection byproducts at eight aquifer storage and recovery sites. Environmental Science & Technology. 2006;40(2):501–8.
- 31. Page D, Dillon P, Toze S, Sidhu J. Characterising aquifer treatment for pathogens in managed aquifer recharge. Water Science and Technology. 2010;62(9):2009–15. pmid:21045325
NRMMC-EPHC-NHMRC. National Guidelines for Water Recycling: Managing Health and Environmental Risks (Phase 1). Canberra: Natural Resource Management Ministerial Council, Environment Protection and Heritage Council, and National Health and Medical Research Council; 2006. https://doi.org/10.2166/wst.2010.380 pmid:20962388
NHMRC-NRMMC. Australian Drinking Water Guidelines. Canberra: National Health and Medical Research Council and Natural Resource Management Ministerial Council; 2011.
WHO. Guidelines for Drinking-water Quality. 4th Edition. Geneva, Switzerland: World Health Organization; 2011.
USEPA. National Primary Drinking Water Regulations. United States Enviromental Protection Agency; 2009.
EU. EU's Drinking Water Standards. European Union; 1998.
ANZECEPH&ARMCANZ. Australian and New Zealand Guidelines for Fresh and Marine Water Quality. Australian and New Zealand Environment and Conservation Council; 2000.
Mackay D, Shui WY, Ma K-C, Lee SC. Handbook Of Physical-Chemical Properties And Environmental Fate For Organic Chemicals. Edition n, editor: CRC Press; 2006.
Drewes JE, Sedlak D, Snyder S, Dickenson E. Indicator and surrogates to assess removal of wastewater-derived contaminants in wastewater treatment and reclamation. Virginia: WateReuse Foundation, 2008.
- 40. Dickenson ERV, Drewes JrE, Sedlak DL, Wert EC, Snyder SA. Applying Surrogates and Indicators to Assess Removal Efficiency of Trace Organic Chemicals during Chemical Oxidation of Wastewaters. Environmental Science & Technology. 2009;43(16):6242–7.
- 41. Wert EC, Rosario-Ortiz FL, Snyder SA. Using Ultraviolet Absorbance and Color To Assess Pharmaceutical Oxidation during Ozonation of Wastewater. Environmental Science & Technology. 2009;43(13):4858–63.
- 42. Gerrity D, Gamage S, Jones D, Korshin GV, Lee Y, Pisarenko A, et al. Development of surrogate correlation models to predict trace organic contaminant oxidation and microbial inactivation during ozonation. Water Research. 2012;46(19):6257–72. pmid:23062789
- 43. Blecken G-T, Zinger Y, Deletić A, Fletcher TD, Hedström A, Viklander M. Laboratory study on stormwater biofiltration: Nutrient and sediment removal in cold temperatures. Journal of Hydrology. 2010;394(3–4):507–14.
- 44. Woltemade CJ, Woodward J. Nitrate Removal in a Restored Spring‐Fed Wetland, Pennsylvania, USA. JAWRA Journal of the American Water Resources Association. 2008;44(1):222–34.
- 45. Hatt BE, Fletcher TD, Deletic A. Hydraulic and Pollutant Removal Performance of Fine Media Stormwater Filtration Systems. Environmental Science & Technology. 2008;42(7):2535–41.
- 46. Li Y, Deletic A, Fletcher T. Modelling wet weather sediment removal by stormwater constructed wetlands: Insights from a laboratory study. Journal of Hydrology. 2007;338(3):285–96.
FAWB. Adoption guidelines for Stormwater Biofilter systems. Facility for Advancing Water Biofiltration, Monash University, 2009.
SCV. Urban Stormwater: Best Practice Environmental Management Guidelines. Melbourne: Stormwater Committee Victoria, 2006.
eWater. Model for urban stormwater improvement conceptualisation (MUSIC) User Manul. eWater Cooperative Research Centre, 2012.
Allison R, Francey M, CSIRO, Melbourne Water. WSUD engineering procedures: stormwater. Collingwood, Victoria, Australia: CSIRO: Melbourne Water; 2005.
Rossman LA. Storm water management model user’s manual. Cincinnati: U.S. Environmental Protection Agency, 2010.
- 52. Park D, Roesner LA. Evaluation of pollutant loads from stormwater BMPs to receiving water using load frequency curves with uncertainty analysis. Water research. 2012;46(20):6881–90. pmid:22578429
- 53. Becouze C, Bertrand-Krajewski J, Dembélé A, Cren-Olivé C, Coquery M. Preliminary assessment of fluxes of priority pollutants in stormwater discharges in two urban catchments in Lyon, France. system. 2009;2:3–10. pmid:20147086
- 54. Birch H, Mikkelsen PS, Jensen J, Lutzhoft . Micropollutants in stormwater runoff and combined sewer overflow in the Copenhagen area, Denmark. Water Science & Technology. 2011;64(2):485–93.
- 55. Bucheli TD, Müller SR, Heberle S, Schwarzenbach RP. Occurrence and behavior of pesticides in rainwater, roof runoff, and artificial stormwater infiltration. Environmental Science & Technology. 1998;32(22):3457–64.
- 56. Cole RH, Frederick RE, Healy RP, Rolan RG. Preliminary Findings of the Priority Pollutant Monitoring Project of the Nationwide Urban Runoff Program. Journal (Water Pollution Control Federation). 1984;56(7):898–908.
- 57. Domagalski J. Pesticides and pesticide degradation products in stormwater runoff: Sacramento Rwer basin, California. JAWRA Journal of the American Water Resources Association. 1996;32(5):953–64.
- 58. Huang X, Pedersen T, Fischer M, White R, Young TM. Herbicide runoff along highways. 1. Field observations. Environmental Science & Technology. 2004;38(12):3263–71.
- 59. Hudak PF, Banks KE. Compositions of first flush and composite storm water runoff in small urban and rural watersheds, north-central Texas. Urban Water Journal. 2006;3(1):43–9.
- 60. Kao C, Wang J, Chen K, Lee H, Wu M. Non-point source pesticide removal by a mountainous wetland. Water Science & Technology. 2002;46(6–7):199–206.
Lamprea K, Ruban V. Micro pollutants in atmospheric deposition, roof runoff and storm water runoff of a suburban Catchment in Nantes, France. 11th International Conference on Urban Drainage; Edinburgh, Scotland, UK2008.
- 62. Polkowska Ż, Grynkiewicz M, Zabiegała B, Namieśnik J. Levels of pollutants in runoff water from roads with high traffic intensity in the city of Gdańsk, Poland. Pol J Environ Stud. 2001;10(5):351–63.
- 63. Polkowska Ż, Tobiszewski M, Górecki T, Namieśnik J. Pesticides in rain and roof runoff waters from an urban region. Urban Water Journal. 2009;6(6):441–8.
- 64. Revitt DM, Ellis JB, Llewellyn NR. Seasonal removal of herbicides in urban runoff. Urban Water. 2002;4(1):13–9.
- 65. Soller J, Stephenson J, Olivieri K, Downing J, Olivieri AW. Evaluation of seasonal scale first flush pollutant loading and implications for urban runoff management. Journal of Environmental Management. 2005;76(4):309–18. pmid:15923077
- 66. Weston D, Holmes R, Lydy M. Residential runoff as a source of pyrethroid pesticides to urban creeks. Environmental Pollution. 2009;157(1):287–94. pmid:18676072
- 67. Zgheib S, Moilleron R, Chebbo G. Influence of the land use pattern on the concentrations and fluxes of priority pollutants in urban stormwater. Water Science & Technology. 2011;64(7):1450–8.
- 68. Zgheib S, Moilleron R, Chebbo G. Priority pollutants in urban stormwater: Part 1—Case of separate storm sewers. Water Research. 2012;46(20):6683–92. pmid:22209279
- 69. Zgheib S, Moilleron R, Saad M, Chebbo G. Partition of pollution between dissolved and particulate phases: What about emerging substances in urban stormwater catchments? Water Research. 2011;45(2):913–25. pmid:20970821
International stormwater BMP database [Internet]. 2014. Available from: www.bmpdatabase.org.
- 71. Björklund K, Cousins AP, Strömvall A-M, Malmqvist P-A. Phthalates and nonylphenols in urban runoff: Occurrence, distribution and area emission factors. Science of The Total Environment. 2009;407(16):4665–72. pmid:19457546
- 72. Clara M, Windhofer G, Hartl W, Braun K, Simon M, Gans O, et al. Occurrence of phthalates in surface runoff, untreated and treated wastewater and fate during wastewater treatment. Chemosphere. 2010;78(9):1078–84. pmid:20096917
HEC. Untreated Highway Runoff in Western Washington. Washington Herrera Environmental Consultants, 2007.
Lopes TJ, Dionne SG. A review of semivolatile and volatile organic compounds in highway runoff and urban stormwater. U.S. Department of the Interior, 1998.
- 75. Rule KL, Comber SDW, Ross D, Thornton A, Makropoulos CK, Rautiu R. Sources of priority substances entering an urban wastewater catchment—trace organic chemicals. Chemosphere. 2006;63(4):581–91. pmid:16216304
- 76. Bressy A, Gromaire MC, Lorgeoux C, Chebbo G. Alkylphenols in atmospheric depositions and urban runoff. Water Sci Technol. 2011;63(4):671–9. pmid:21330713
- 77. Bressy A, Gromaire MC, Lorgeoux C, Saad M, Leroy F, Chebbo G. Towards the determination of an optimal scale for stormwater quality management: Micropollutants in a small residential catchment. Water Research. 2012;46(20):6799–810. pmid:22204938
Dugan GL, Christakos CE. Water Quality of Airport Storm Runoff WRRC technical report 153. Water Resources Research Center, University of Hawaii at Manoa, 1983.
- 79. Fries E, Püttmann W. Occurrence of 4-Nonylphenol in rain and snow. Atmospheric Environment. 2004;38(13):2013–6.
- 80. Grynkiewicz M, Polkowska Z, Kot-Wasik A, Namiesnik J. Determination of phenols in runoff. Polish Journal of Environmental Studies. 2002;11(1):85–9.
Norton DE. Chemical Contaminants in Surface Runoff from the Abandoned Cascade Pole (Olympia) Wood Treating Facility. Washington: Washington State Department of Ecology, Environmental Investigations and Laboratory Services Program, Toxics Investigations/Ground Water Monitoring Section; 1990.
- 82. Hwang H- M, Foster GD. Polychlorinated biphenyls in stormwater runoff entering the tidal Anacostia River, Washington, DC, through small urban catchments and combined sewer outfalls. Journal of Environmental Science and Health. 2008;43(6):567–75. pmid:18393063
- 83. Rossi L, de Alencastro L, Kupper T, Tarradellas J. Urban stormwater contamination by polychlorinated biphenyls (PCBs) and its importance for urban water systems in Switzerland. Science of The Total Environment. 2004;322(1–3):179–89. pmid:15081754
Delzer GC, Zogorski JS, Lopes TJ, RLB. Occurrence of the gasoline oxygenate MTBE and BTEX compounds in urban stormwater in the United States, 1991–95. California: U.S. Department of the Interior, 1996.
- 85. Svensson T, Laturnus F, Sandén P, Öberg G. Chloroform in Runoff Water: A Two-Year Study in a Small Catchment in Southeast Sweden. Biogeochemistry. 2007;82(2):139–51.
- 86. Borden RC, Black DC, McBlief KV. MTBE and aromatic hydrocarbons in North Carolina stormwater runoff. Environmental Pollution. 2002;118(1):141–52. http://dx.doi.org/10.1016/S0269-7491(01)00204-4. pmid:11996377
- 87. Lopes TJ, Fallon JD, Rutherford DW, Hiatt MH. Volatile organic compounds in storm water from a parking lot. Journal of Environmental Engineering. 2000;126(12):1137–43.
Torres C. Characterization and pollutant loading estimation for highway runoff in omaha, Nebraska. Nebraska: University of Nebraska-Lincoln; 2010.
- 89. Drapper D, Tomlinson R, Williams P. Pollutant concentrations in road runoff: Southeast Queensland case study. Journal of Environmental Engineering. 2000;126(4):313–20.
- 90. James R, Wilbon P, DiVincenzo J. Pervious and Impervious Urban Stormwater Runoff in a Rapidly Urbanizing Region: Occurrence of Fluoranthene and Pyrene. Bull Environ Contam Toxicol. 2010;85(1):32–6. pmid:20431866
- 91. Hwang H-M, Foster GD. Characterization of polycyclic aromatic hydrocarbons in urban stormwater runoff flowing into the tidal Anacostia River, Washington, DC, USA. Environmental Pollution. 2006;140(3):416–26. pmid:16213639
- 92. Kim L-H, Kayhanian M, Zoh K-D, Stenstrom MK. Modeling of highway stormwater runoff. Science of The Total Environment. 2005;348(1–3):1–18. http://dx.doi.org/10.1016/j.scitotenv.2004.12.063. pmid:16162328
- 93. Kumata H, Masuda K, Yamada J, Takada H. Water-particle distribution of hydrophobic micro pollutants in storm water runoff. Polycyclic Aromatic Compounds. 2000;20(1–4):39–54.
- 94. Lamprea K, Ruban V. Characterization of atmospheric deposition and runoff water in a small suburban catchment. Environmental Technology. 2011;32(10):1141–9. pmid:21882566
- 95. Mahler BJ, Van Metre PC, Bashara TJ, Wilson JT, Johns DA. Parking Lot Sealcoat: An Unrecognized Source of Urban Polycyclic Aromatic Hydrocarbons. Environmental Science & Technology. 2005;39(15):5560–6.
- 96. Menzie CA, Hoeppner SS, Cura JJ, Freshman JS, LaFrey EN. Urban and suburban storm water runoff as a source of polycyclic aromatic hydrocarbons (PAHs) to Massachusetts estuarine and coastal environments. Estuaries. 2002;25(2):165–76.
- 97. Stein ED, Tiefenthaler LL, Schiff K. Watershed-based sources of polycyclic aromatic hydrocarbons in urban storm water. Environmental Toxicology and Chemistry. 2006;25(2):373–85. pmid:16519297
- 98. Watts AW, Ballestero TP, Roseen RM, Houle JP. Polycyclic Aromatic Hydrocarbons in Stormwater Runoff from Sealcoated Pavements. Environmental Science & Technology. 2010;44(23):8849–54.